42 Total ReviewsB&B Heating & Cooling, Inc.708-403-2276$13010 W 159th St Ste 1, Homer Glen IL
Furnace Service And Repair Chicago, Illinois
If your gas furnace in Chicago, IL is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Chicago, IL. B&B Heating & Cooling, Inc. has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on B&B Heating & Cooling, Inc. to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
Recent Furnace Service And Repair Chicago, Illinois by B&B Heating & Cooling, Inc.
GoodmanGMS80804B Upon arrival the Tech. found the furnace turned Chicago,
LennoxML195UH090XP36CCondensing Gas Furnace Upon arrival the Tech. found the furnace not operating properly due to a dirty flame sensor and furnace. The Tech. cleaned the furnace and flame sensor. The Tech. also found the female terminal connector at the flame sensor, the Tech. repaired the connection at the flame sensor. The furnace was fully operational at departure. Chicago,
Nordyne Heating & AirG6RA096C-16 Upon arrival the Tech. found furnace fully operational. There are no supply dampers throughout the ductwork. Recommending two portable units that supply heat and a/c. Also, there is a substantial buildup of debris inside the ducts and branches. Recommending a duct cleaning. The Tech. found a very old and dirty furnace filter, changed the 16x25x1 furnace filter. The furnace was fully operational at departure. Chicago,
LennoxML180UH090P48B Upon arrival the Tech. Inspected all registers that the resident complained were no longer adjustable. They are in fact broken, however, there were dampers in the supply trunk to the second floor that were adjusted to reduce air flow and the resident was satisfied with this. The furnace was also fully operational at departure. Chicago,