American Standard HVAC 2A7A10?0A1000AA
Upon arrival the Tech. found the American Standard AC system not operating properly due to broken wires and pitted contactor. Repaired 2-wire and replaced 30amp contactor. The AC system was fully operational at departure.
Upon arrival the Tech. found the Carrier AC system working properly. There was water in the bottom cabinet and the Tech. believes when the A-Coil thawed out the IFC board had gotten wet and the fan shut off. The AC system was working at departure. Unit stopped working as the Tech. was leaving. It was blowing air indoors but the compressor would shut off while the condenser fan would stay running. After a couple of minutes it would come back up and run and coil as it should. Checked all the electrical components and they are within specs. The AC was fully operational at departure.