Furnace Repair in Plainfield, Illinois
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Plainfield, IL is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call B&B Heating & Cooling, Inc. now. We fix broken heating equipment all the time in Plainfield, IL. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
Upon arrival the Techh. found the Bryant furnace from 2004 ws inoperable due to a faulty Ignitor and a low flame signal. Replace the Igniter and cleaned the furnace and flame sensor, the unit was fully operational at departure.
Upon arrival the Tech found the Tappen Furnace operating but the circuit board was not wired properly. Corrected witing to circuit board ant furnace. Cl;eaned Furnace and Flame Sensor. AC was running at the same tome as furnace due to a bad 40 amp contactor on AC condenser - Repalced Contactor. The Unit was fully operational at departure.
Upon arrival the Tech. found the Goodman furnace not igniting. Found a faulty HSI. The HSI needed to be replaced.Also there was a low flame signal - Cleaned the Furance and Flame Sensor.