Furnaces can be intimidating especially when they're not working. However there might be a silver lining to this stressful situation: roughly a quarter of all service calls can be resolved with easy fixes that are simple and inexpensive.
At B&B Heating & Cooling, Inc. we help homeowners like you in Westchester, IL all the time with their heating systems. From simply offering advise, to complete system replacement, we have the knowledge and experience to help you resolve the challenges your heating system is presenting in the best possible way.
Upon arrivla the Tech. found the radiant zone for the lower level (in floor radiant) isolated that zone and bled to make sure it was not air bound. Found no air in system. Pump for that zone does not always stay on. Tested pump relay - all ok. Found thermostat does not always make good contact. Repalced Thermostat. Westchester, IL 03-21-2019
Upon arrival the Tech. found the Aire Flow furnace from 2013 not operating properly due to a low flame signal. Cleaned the furnace and flame sensor. Checked air filter and cleared debris from inducer port.
Westchester, IL 04-16-2019