American Standard HVAC 2A7A2024A1000AA
Upon arrival the Tech. found both AC systems not working.
The Second floor cap and hard start kit needed to be replaced.
The main floor unit has a bad contactor. Replaced contactor.
Upon arrival the Tech. found the furnace vibrating badly when the AC comes on. Removed Blower Assembly and found cardboard stuck in Blower Wheel. Cleared out debris and ran system. The AC was fully operational at departure.
Upon arrival the Tech. found the Goodman Ac system operating properly. Inspected refrigerant levels, all electrical components , thermostat, supply temperatures and supply air volume. Cleaned the Condenser and advised the custoemr that the 2-1/2 ton unit is onyl designed for a 15-20 degree difference from the ambient temperature. Customer is trying to attempt a 64 degree set point.