No Heat in Bolingbrook, Illinois
Furnaces can be intimidating especially when they're not working. However there might be a silver lining to this stressful situation: roughly a quarter of all service calls can be resolved with easy fixes that are simple and inexpensive.
At B&B Heating & Cooling, Inc. we help homeowners like you in Bolingbrook, IL all the time with their heating systems. From simply offering advise, to complete system replacement, we have the knowledge and experience to help you resolve the challenges your heating system is presenting in the best possible way.
Found furnace inoperable due to a hole inside the heat exchanger. Replaced furnace and installed a Lennox 70,000 Upflow
Upon arrival theTech found the Furnace was fully operational. The dampers have been adjusted. Set the thermostat to "fan on" to get better air flow.
Upon arrival the Tech. found the Armstrong Furnace not working due to batteries not installed properly. Found the furnace had a low flame signal and needed to be cleaned. When fired up - the blower housing was loose - tighten the bolts on Blower housing. - The furnace was fully operational at departure.
Upon arrival the tech. found unit not calling "w" wire at IFC board was not secured behind terminal on board. Tighten wire connection, found unit had low flame signal. Cleaned furnace
Upon arrival the Tech. found the Rheem Furnace from 2003 had a bad Blower Motor. The Blower Motor & Capacitor will need replacement.