44 Total Reviews/files//bb-heating-cooling-logo.png708-403-2276$13010 W 159th St Ste 1, Homer Glen IL
Furnace Service And Repair Aurora, Illinois
If your gas furnace in Aurora, IL is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Aurora, IL. B&B Heating & Cooling, Inc. has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on B&B Heating & Cooling, Inc. to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
Recent Furnace Service And Repair Aurora, Illinois by B&B Heating & Cooling, Inc.
LennoxML180UH090P48B - Upon arrival the Tech. found the Carrier Furnace from 1992 was not running due to a bad Inducer Motor.
- The Heat Exchanger was inspected, and cracks were found.
* The Furnace needs to be replaced due both to condition & age. Aurora,
GoodmanGMS80804B Complaint of No Heat.
- Upon arrival the Tech. found the furnace not operating properly due to a faulty gas valve. The Tech. replaced the gas valve and cleaned the furnace and flame sensor. The furnace was fully operational at departure. Aurora,
Armstrong HVACA80UH1D070A12 Upon arrival the Tech. found the furnace not operating properly due to a dirty flame sensor. The Tech. cleaned the furnace and flame sensor. The Tech. also found the furnace had a Add-A-Wire that was loose at the terminal board. The Tech. repaired the wires and tested the operation of the furnace. The furnace was fully operational at departure. Aurora,